Change Notice 03-033
Issue Date: 09/09/03
NRC INSPECTION MANUAL IIPB
This page includes links to files in non-HTML format. See Plugins, Viewers, and Other Tools for more information.
|TRAINING: ||No special training requirements have been identified for any documents issued with this change notice. |
|REMARKS: || |
IMC 2515, Appendix D (Plant Status) has been revised to provide improved guidance to an inspector on the requirement to inform the Materials and Chemical Engineering Branch, NRR, of steam generator tube leaks of greater than 3 gallons per day.
IP 71111.08 (Inservice Inspection Activities) has been revised to add guidance on steam generator tube primary-to-secondary leakage. This guidance used to be contained in Part 9900.
9900 Technical Guidance-Mechanical (Steam Generator Tube Primary-To-Secondary Leakage) has been revised to remove inspector actions for leakage greater than 3 gallons per day. The inspector actions have been moved to IP 71111.08, Inservice Inspection Activities. Section 9900 is only for inspector guidance.
Page Last Reviewed/Updated Monday, April 09, 2018