|TECHNICAL SPECIFICATION REQUIRED SHUTDOWN DUE TO INOPERABLE BORON INJECTION FLOW PATHS AND CHARGING PUMPS
"On July 31, 2019, at 1206 CDT, Waterford 3 commenced initiation of a plant shutdown as required by Technical Specification (TS) Limiting Condition for Operation (LCO) 3.0.3. Prior to this, on July 31, 2019, at 1108 CDT, the boron injection flow paths were declared inoperable in accordance with LCO 220.127.116.11, 'Flow Paths - Operating,' and the charging pumps were declared inoperable in accordance with LCO 18.104.22.168, 'Charging Pumps-Operating.' This was due to visual examination identifying that propagation had progressed on a previously identified flaw on piping upstream of the header supplying the charging pumps. TS LCO 3.0.3 was entered due to the action statements of LCOs 22.214.171.124 and 126.96.36.199 not being met. LCO 3.0.3 requires that action shall be initiated within one hour to place the unit in a mode in which the specification does not apply by placing it in hot standby within the next 6 hours and cold shutdown within the next 30 hours. At 1206 CDT, Waterford 3 commenced direct boration to the reactor coolant system.
"This condition meets the reporting criteria of 10 CFR 50.72(b)(2)(i) due to the initiation of plant shutdown required by Technical Specifications and 10 CFR 50.72(b)(3)(v)(A) and (D) due to an event or condition that could have prevented fulfillment of a safety function of structures or systems that are needed to (A) shutdown the reactor and maintain it in a safe shutdown condition and (D) mitigate the consequences of an accident."