Part 21 Report - 2001-051
A SCANA COMPANY
||Stephen A. Byrne
Vice President, Nuclear Operations
||March 15, 2001
Document Control Desk
U. S. Nuclear Regulatory Commission
Washington, DC 20555
||VIRGIL C. SUMMER NUCLEAR STATION DOCKET NO.50/395
OPERATING LICENSE NO. NPF-12 FINAL REPORT PURSUANT TO 10 CFR PART 21 (SSH 2000-001)
South Carolina Electric & Gas (SCE&G) submits this letter in accordance with the requirements of 10 CFR 21.21 (a)(2) as a final report of an identified defect which was potentially associated with a substantial safety hazard.
On 10/12/00, at 0630 hours, visual inspection revealed small amounts of boron buildup on the weld between the vessel nozzle and the hot leg pipe. Within hours, the suspect area was cleaned and a dye penetrant (PT) examination of the pipe identified a 4 inch indication at the weld between the hot leg piping and the reactor vessel nozzle. The weld is located approximately 3 feet from the vessel in pipe near the nozzle. The indication was located about 17" from the top of the pipe. This pipe has a nominal inside diameter of 29 inches and is approximately 2.5 inches thick.
Subsequent ultrasonic examination from the inside diameter identified an axial flaw less than 3 inches long. The same examination determined that the original indication was not the source of the leak.
The interim 10 CFR Part 21 report (RC-00-0368) was submitted to allow additional evaluation and cause determination.
NUCLEAR EXCELLENCE - A SUMMER TRADITION!
SCE&G I Virgil C. Summer Nuclear Station ? P.O. Box 88 ? Jenkinsville, South Carolina 29065 ? T (803)345.5209 ? www.scana.com
SC E&G Engineering review of the Root Cause Evaluation Report for potential 10 CFR Part 21 concerns, has determined that a Significant Safety Hazard did not exist. Attached is the engineering justification for this position.
Should you have any questions, please call Mr. Jeffrey Pease at (803) 345-4124.
||Very truly yours,
Stephen A. Byrne
||N. O. Lorick
N. S. Cams
T. G. Eppink
R. J. White
L. A. Reyes
K. R. Cotton
J. B. Knotts, Jr.
NRC Resident Inspector
G. G. Williams
RTS (SSH 2000-001)
Page Last Reviewed/Updated Friday, April 17, 2020