|AUTOMATIC REACTOR TRIP
"On March 23, 2020, at 1013 EDT, with Harris Nuclear Plant Unit 1 in Mode 1, at 100 percent power, an unplanned actuation of the reactor protection system occurred. This resulted in an automatic reactor trip. The trip occurred during the restoration of the auto-stop turbine trip function during a planned maintenance evolution.
"All safety systems functioned as expected. Auxiliary Feedwater started as designed and was secured. Steam generator levels are being maintained by normal feedwater through the feedwater regulator bypass valves. Decay heat is being removed by using the condenser steam dump flow path.
"Due to the unplanned Reactor Protection System actuation while critical and the expected Auxiliary Feedwater actuation, this event is being reported as a four hour, non-emergency notification per 10 CFR 50.72(b)(2)(iv)(B) and an eight hour, non-emergency notification per 10 CFR 50.72(b)(3)(iv)(A).
"There was no impact on the health and safety of the public or plant personnel.
"The NRC Resident Inspector has been notified."