| 60-DAY OPTIONAL TELEPHONIC NOTIFICATION DUE TO AN INVALID ACTUATION OF A CONTAINMENT ISOLATION SIGNAL|
"This 60-day telephone notification is being made per the reporting requirements specified by 10 CFR 50.73(a)(2)(iv)(A) and 10 CFR 50.73(a)(1) to describe an invalid actuation of a general containment isolation signal affecting more than one system.
"On July 31, 2019, at approximately 1650 hours Central Daylight Time (CDT), Browns Ferry Nuclear Plant (BFN), Unit 1 experienced a Primary Containment Isolation System (PCIS) Group 6 isolation during performance of surveillance procedure 1-SR-126.96.36.199.3(A), Reactor/Refueling Zone Ventilation Radiation Monitor 1-RM-90-140/142 Calibration and Functional Test. The Group 6 isolation caused the initiation of Standby Gas Treatment (SBGT) Trains A, B, and C, and Control Room Emergency Ventilation (CREV) subsystem B. Unit 1 H2O2 Analyzer and Drywell Radiation Monitor CAM, 1-RM-90-256, were declared Inoperable and Technical Specifications (TS) Limiting Condition for Operation (LCO) 3.4.5 Condition B was entered. All affected safety systems responded as expected.
"Plant conditions which initiate PCIS Group 6 actuations are Reactor Vessel Low Water Level (Level 3), High Drywell Pressure, or Reactor Building Ventilation Exhaust High Radiation (Reactor Zone or Refuel Zone). At the time of the event, these conditions did not exist; therefore, the actuation of the PCIS was invalid.
"This condition was the result of two cleared fuses in the alarm logic. The apparent cause is a ground fault on the A6 Open Drain Input/Output Module.
"There were no safety consequences or impact to the health and safety of the public as a result of this event.
"This event was entered into the Corrective Acton Program as Condition Report 1537358.
"The NRC Resident Inspector has been notified of this event."