EN Revision Imported Date : 3/5/2019
EN Revision Text: INTERIM PART 21 REPORT - EVALUATION OF MOTORS
The following information was received by from ABB Motors and Mechanical INC by facsimile:
"Pursuant to 10 CFR 21.21(a)(2) this letter provides an interim report concerning an evaluation being performed by ABB Motors and Mechanical Inc. (formerly Baldor Electric Company) on three 40 ft-lb, 56 frame, 2-pole AC electric motors. The issue being evaluated pertains to the abnormal appearance of cracked paint and minor deformation around the stator pin which is located in the motor housing shell.
"The three motors were supplied to Flowserve - Limitorque on a single purchase order in April 2013. The issue being evaluated was identified after MOV production set-up and testing at the valve manufacturing facility. The equipment had not been supplied to a nuclear power plant and thus had not been placed into service.
"The discovery date of the condition being evaluated is August 2, 2018. Evaluation of reportability cannot be completed within the initial evaluation period due to the need to perform additional inspections of motors manufactured in the same period. ABB is working with Flowserve - Limitorque to expedite the additional inspections and testing. It is anticipated that this will be completed by 01/11/2019.
"An initial review of ABB's records indicate that since 1998 ABB has supplied approximately 670, 56-frame AC electric motors of 40 and 60 ft-lb. to Flowserve - Limitorque. Flowserve - Limitorque communicated to ABB that there have been no previously reported occurrences of this issue nor any reported motor failures related to this issue.
"(i) Name and address of the individual or individuals informing the Commission.
ABB Motors and Mechanical Inc.
Flowery Branch, GA 30542
(678) 947 7350
"(ii) Identification of the facility, the activity, or the basic component supplied for such facility which fails to comply or contains a defect.
"The basic components being evaluated are Class 1E 40 ft-lb, 56 frame, 2-pole motors supplied to Flowserve - Limitorque for installation on valve actuators to be supplied into nuclear plant applications, to date, no basic components have been determined to contain a defect.
"(iii) Identification of the firm constructing the facility or supplying the basic component which fails to comply or contains a defect.
"The basic components being evaluated were supplied by ABB Motors and Mechanical Inc. (formerly Baldor Electric Company) ("ABB"), No basic components have been determined to contain a defect. This is an interim report.
"(iv) Nature of the defect or failure to comply and the safety hazard which is created or could be created by such defect or failure to comply
"ABB was contacted by our customer Flowserve - Limitorque regarding three 40 ft-lb, 56 frame, 2-pole AC electric motors which were reported to have an abnormal visual appearance of cracked paint and minor deformation of the motor housing material around the stator pin. The motor stator pin is installed through the motor housing shell into the stator assembly. ABB's initial inspection of the three motors suggested that the deformation around the pin may have occurred when the motor was operated during actuator and/or MOV production testing. ABB is evaluating whether this abnormal condition of the stator pin interface with the motor frame constitutes a defect that could potentially affect the safety related function of the motor. To date, no basic components have been determined to contain a defect. This is an interim report.
"(v) The date on which the information of such defect or failure to comply was obtained.
"The discovery date of the condition being evaluated is August 2, 2018,
"(vi) In the case of a basic component which contains a defect or fails to comply, the number and location of these components in use at, supplied for, being supplied for, or may be supplied for, manufactured, or being manufactured for one or more facilities or activities subject to the regulations in this part.
"At this time, no basic components have been determined to contain a defect.
"(vii) The corrective action, which has been, is being, or will be taken; the name of the individual or organization responsible for the action; and the length of time that has been or will be taken to complete the action.
"None at this time,
"(viii) Any advice related to the defect or failure to comply about the facility, activity, or basic component that has been, is being, or will be given to purchasers or licensees.
"None at this time."
* * * UPDATE AT 0815 EST ON 1/11/2019 FROM SHELDON THOMAS TO MARK ABRAMOVITZ * * *
The following information was received via fax:
"This letter is a follow-up to the initial Interim Notification dated October 12, 2018 (Ref. ML18302A229).
ABB continues to work with Flowserve-Limitorque to expedite the additional inspections of motors in the field and testing of motors pulled from inventory. The testing is necessary to assist in determination if the abnormal appearance and deformation constitutes a defect which would cause a substantial safety hazard.
"It is anticipated that this will be completed by February 28, 2019. At that time, motor testing should be complete and analysis of results conducted. ABB will then be able to determine if the nature of the condition is a substantial safety hazard and reportable. If further time is necessary for evaluation, a follow-up to this report will be filed.
"Since discovery of the condition, and to the date of this report, ABB and Flowserve-Limitorque are not aware of any confirmed field inspections by Flowserve-Limitorque's customer or the results of such inspections."
Notified the R1DO (Bower) and Part 21 Reactors Group (via e-mail).
* * * CLOSEOUT RECEIVED AT 1642 EST ON 3/4/20119 FROM SHELDON THOMAS TO MARK ABRAMOVITZ * * *
The following closeout was received by fax:
"ABB has completed the evaluation of the abnormal appearance of the three motors identified in this notification with the determination that this condition does not constitute a defect that would affect the safety related function of the motor."
Notified the R1DO (Werkheiser) and Part 21 Reactors Group (via e-mail).