|PART 21 - COMPONENTS PROVIDED AS SAFETY-RELATED SPARE PARTS WITHOUT BEING DEDICATED
"AMETEK Solidstate Controls (SCI) is providing this report in accordance with 10CFR Part 21 as notice of a process defect that resulted in components being provided as safety-related spare parts without being dedicated.
"PROBLEM DESCRIPTION: Lack of evidence of dedication testing for AMETEK Solidstate Controls Safety-Related Operational Spare Parts Kits provided with SCI equipment
"CAUSE: In October 2018, NextEra Seabrook notified SCI of a part number discrepancy with a safety-related fuse that was provided with an operational spare parts kit with an equipment order. After further investigation, it was determined that dedication testing was not performed on the operational spare parts kits provided with the equipment on various jobs in recent years.
"Generally, spare parts are ordered separately from equipment and a process is in place to direct the parts to quality for commercial grade dedication testing. In this instance, the parts were ordered as a line item on the sale and the parts in question were selected from inventory without being routed through quality for commercial grade dedication.
"PROBLEM YOU COULD SEE: Evidence of dedication testing is not available for operational spare parts kits which were provided with equipment orders, however, there are no functional concerns with the components provided on these orders. The parts would have been selected at the same time as the parts that were installed in the systems. Additionally, for the commercial grade items provided, there is no history of failure during
dedication testing performed by AMETEK either in equipment or during bench testing.
"ACTION REQUIRED: Aside from printed circuit boards, the parts supplied as operational spare parts will need to be dedicated. AMETEK SCI recommends returning the untested items and will work with [the customer] to arrange returns and retesting. Please contact Mr. Mark Shreve of AMETEK SCI's Client Services group at 1-800-222-9079, 1-614-846-7500 ext. 6332, or email@example.com."
The non-dedicated parts were supplied to Brunswick Steam Electric Plant, Seabrook Station, and North Anna Power Station. In addition, non-dedicated parts were also supplied to the Krsko Nuclear Power Plant in Slovenia and the Maanshan Nuclear Power Plant in Taiwan.
* * * UPDATE ON 1/31/19 AT 1304 EST FROM ETHAN SALSBURY TO OSSY FONT * * *
The following was received via email from Ametek:
"After further evaluation, [Ametek] has determined that additional kits are impacted by this issue, but the same customer list and POs apply. No additional customers are impacted and a corrected notification will be provided to customers that have been previously identified."
R1DO (Bickett) and R2DO (Lopez) were notified. Part 21 Reactors Group was notified via email.