Home > NRC Library > Training Courses > NRC Reactor Concepts (R-100) Training Course > Videos
[Time Stamp: 00:13] The following comments on the Soviet report on the accident are from a Japanese national television report.
[Time Stamp: 00:21] A Russian report said that the accident was caused by violations of operational procedures.
[Time Stamp: 00:28] But let's examine that and see if it really was due to an operator's error.
[Time Stamp: 00:33] The first violation: April 25th 1400 hours: The bypassing of the emergency core cooling system.
[Time Stamp: 00:42] Before the experiment, if the ECCS is not bypassed, the reactor will shutdown and the experiment cannot be run.
[Time Stamp: 00:53] In order to continue the experiment, they have to shut off the device.
[Time Stamp: 00:58] Therefore, we cannot say this is an operator's error.
[Time Stamp: 01:03] The second violation: April 26th 0 hours and 28 minutes AM: automatic control conversion.
[Time Stamp: 01:13] Since the operator did not switch on the device which keeps the power at a constant level, the power dropped and the reactor became unstable.
[Time Stamp: 01:24] This was obviously an operation error.
[Time Stamp: 01:28] The third violation: the control rods were pulled out too far.
[Time Stamp: 01:33] They wanted to experiment at a low power output, but they had brought the power too far down.
[Time Stamp: 01:39] In keeping with the character of this reactor, in order to maintain the power, they had no other way but to pull out the control rods.
[Time Stamp: 01:47] Whatever person ordered the continuation of this experiment is responsible.
[Time Stamp: 01:52] Therefore, it is not the operator's error.
[Time Stamp: 01:56] The fourth violation: One hour 3 to 7 minutes: the addition of main circulation pumps.
[Time Stamp: 02:05] The fourth violation was caused by the addition of two pumps which supplied coolant to the core.
[Time Stamp: 02:11] This caused an excess flow of coolant, which in turn caused the core to become unstable.
[Time Stamp: 02:17] It was planned in the experiment, therefore it is not an operation error.
[Time Stamp: 02:23] Fifth violation: one hour nineteen minutes 58 seconds: the bypassing of the automatic shutdown for the steam separator.
[Time Stamp: 02:33] This was ordered for the continuation of the experiment.
[Time Stamp: 02:36] Therefore it is not the operator's error.
[Time Stamp: 02:40] The sixth violation: one hour twenty-three minutes 4 seconds: the bypassing of the automatic shutdown system of the reactor
[Time Stamp: 02:50] As the turbine slows down, a signal is given to automatically shutdown the reactor.
[Time Stamp: 02:56] This was bypassed, in order to be able to repeat the experiment.
[Time Stamp: 03:00] It was not in the experimental procedures.
[Time Stamp: 03:03] It is the responsibility of the person who forcefully tried to continue the experiment.
[Time Stamp: 03:09] If we examine these six violations, there are only two operator errors.
[Time Stamp: 03:14] A bigger problem is the characteristic of the reactor becoming unstable at low power.
[Time Stamp: 03:20] Despite this characteristic, they forcefully continued this experiment.