Safety Evaluation Report Related to the Operation of Watts Bar Nuclear Plant, Units 1 and 2 (NUREG-0847, Supplement 17)
On this page:
Download complete document
This page includes links to files in non-HTML format. See Plugins, Viewers, and Other Tools for more information.
Date Published: October 1995
Docket Nos. 50-390 and 50-391: Tennessee Valley Authority
Office of Nuclear Reactor Regulation
U.S. Nuclear Regulatory Commission
Washington, DC 20555-0001
This report supplements the Safety Evaluation Report (SER), NUREG-0847 (June 1982), Supplement No. 1 (September 1982), Supplement No. 2 (January 1984), Supplement No. 3 (January 1985), Supplement No. 4 (March 1985), Supplement No. 5 (November 1990), Supplement No. 6 (April 1991), Supplement No. 7 (September 1991), Supplement No. 8 (January 1992), Supplement No. 9 (June 1992), Supplement No. 10 (October 1992), Supplement No. 11 (April 1993), Supplement No. 12 (October 1993), Supplement No. 13 (April 1994), Supplement No. 14 (December 1994), Supplement No. 15 (June 1995), and Supplement No. 16 (September 1995) issued by the Office of Nuclear Reactor Regulation of the U.S. Nuclear Regulatory Commission with respect to the application filed by the Tennessee Valley Authority, as applicant and owner, for licenses to operate the Watts Bar Nuclear Plant, Units 1 and 2 (Docket Nos. 50-390 and 50-391). The facility is located in Rhea County, Tennessee, near the Watts Bar Dam on the Tennessee River. In this supplement, NRC examines the significant problems of construction quality and quality assurance effectiveness that led TVA to withdraw its certification in 1985 that Watts Bar Unit 1 was ready to load fuel. Also discussed are the extensive corrective actions performed by TVA according to its nuclear performance plans and other supplemental programs, and NRC's extensive oversight to determine whether the Watts Bar Unit 1 construction quality and TVA's operational readiness and quality assurance effectiveness are adequate for a low-power operating license to be issued. SSER 17 does not address Watts Bar Unit 2, except for the systems which are necessary to support Unit I operation.