Acceptance and Verification For Early Warning Fire Detection Systems (NUREG/CR-1798)
On this page:
Download complete document
This page includes links to files in non-HTML format. See Plugins, Viewers, and Other Tools for more information.
J.L. Boccio and R.E. Hall Brookhaven National Laboratory
Upton, New York 11973 and
I. Asp Gage-Babcock and Associates, Inc.
Mount Kisco, New York 10549
Prepared for the
U.S. Nuclear Regulatory Commission
Washington, D.C. 20555
Under Interagency Agreement DE-ACO2-76CH00016
NRC FIN NO. A-3335
This report has been written to provide an interim guide accounting for the basic factors that should be considered in formulatina a fire detection system selection criteria and the verification of such a system. The fire detection system selection criteria that is proposed here still requires a viable mix of good engineering judgement, the use of qualified investigators, and excellent reporting and administrative procedures; all of which should be coupled to the results of current research that has been discussed herein. The fire detection analysis should address five major phases required in a fire detection analysis, viz, (1) establishing area detector requirements, (2) selection of specific detector types, (3) location and spacing of detectors, (4) installation tests and maintenance, and (5) administrative controls and reporting.